Paros-Serie – air/water inverter heat pumps for indoor installation
Article Number 1008004101
The adaptable one.
Application limit heating water supply temperature 20°C to 60°C
Recommended application range heat source -22°C to 35°C
The units are recommended for the following total building power requirements:
approx. 4-5 kW
For faster installation, the system is factory-equipped with the following components:
- Luxtronik 2.1 heat pump controller as wall controller with integrated heating controller
- Electrical connection ready for plug-in (electrical connection set must be ordered separately as a functional accessory) incl. all refrigeration safety devices
- Circulation pump for heating and domestic hot water preparation (functionally necessary)
- Outdoor sensor
- Optionally suitable for cooling up to +7 °C flow temperature. Cooling is deactivated at the factory and can be deactivated by the activated by the installer during commissioning
- Filled with fluorinated greenhouse gas R454B
- Heat metering to meet BEG guidelines (not for operating cost billing).
Wall controller - WR 4
Hydraulic module - HV 4
Hydraulic station - HSV 4
|Equipment designation||Paros 4-1|
|Capacity for heating (kW)||2,17 (A2/W35 part. load)|
|Capacity for heating 2 (kW)||3,47 (A7/W35 part.load)|
|COP||4,1 (A2/W35 part. load)|
|COP 2||4,84 (A7/W35 part. load)|
|Max. flow temperature||60|
|Indoor/ Outdoor installation||Innenaufstellung|
|Seasonal space heating energy efficiency ƞs (35°C)||180,1|
|Seasonal space heating energy efficiency ƞs (55°C)||137,8|
|Seasonal water heating energy efficiency class(the package of combination heater, temperature control and solar device)||A|
The operating instructions of the functionally necessary accessories such as hydraulic module or hydraulic station are stored in the "Downloads" tab under "ACCESSORIES".
* The data are only recommendations. Depending on individual circumstances, a heat pump with a lower heating capacity may also be suitable for larger buildings and vice versa. In addition, it is possible to connect several heat pumps together and thus increase the heating capacity. Finally, a precise individual calculation is required to select the really suitable system for the project.
Possible energy efficiency classes
Space heaters (35° C, 55° C): A+++ to D Ӏ Combined space heaters: A+++ to G Ӏ Combi heaters: A+++ to D Ӏ Hot water preparation: A+ to F Ӏ Combination combi heaters: A+++ to G Ӏ Hot water tanks: A+ to F Ӏ Domestic hot water preparation: A+ to F Ӏ Ventilation: A+ bis G
Technical changes and errors excepted